HEPA / ULPA Quantity Design Guidelines
For the Semiconductor/Auto/Electronic/Mems/industries:
|Quantities and Percentage
|Fed 209E English
|Fed 209E Metric
of HEPA/ULPA Ceiling
|4% diffused air
|10% recommended diffused air
|27% recommended laminar flow air
|54% laminar flow air
|90% laminar flow air
|100% laminar flow air
Ceiling Coverage Calculations
To determine the recommended ceiling coverage required with 2' x 4' HEPA’s or ULPA’s divide the square foot of the cleanroom by eight (2' x 4') then multiply the recommended percentage and that will provide you with the quantity of units needed.
Note: The recommended quantities are for reference only. They are based on optimum room layout and design to obtain certain class cleanrooms with a minimal amount spent on filtration. The arrangement and spacing of filtration are one of the most crucial characteristics of cleanroom design. Equipment layout return air grills and personnel have a profound impact on the fluid dynamics of the room. Cleanroom protocol and maintenance are also key factors in ensuring constant contamination control to desired specifications.
For the Medical Device/Bio Sciences/Pharma
|Room Air Changes Per hour
|Max # of 2x4 opening
|HEPA Filters needed
|CFM per HEPA
|Filter face velocity
|Estimated Watts per FFU 95
|Face Area of each HEPA
|Energy Cost ($/kWh)
|Hours of operation per year
When designing the HEPA/ULPA location, you must be cognizant of the room furniture and equipment/tool layout. This will drastically affect the fluid dynamics of the room and may create grey zones and migrating of particles into dead zones. It will also affect the flow to the low air wall returns or diminish the raised floor capability to pull air evenly throughout the cleanroom.
The arrangement and spacing of the HEPA/ULPA filters are the MOST important aspect of the cleanroom/Lab design. It can make the room fail in testing or worse yet, it will pass but have areas where your product gets contaminated unbeknownst to you until it is too late.
Welcome to our reference library. Over the years we have learned many things about general construction, more specifically cleanroom design and general construction design. Here you can find articles and reference information covering a wide variety of topics. Cleanroom construction, tenant improvement, and ADA compliance are just a few of the topics covered here. If you have any comments or would like more information on any of the articles contained here, please use our contact us page to send us an email and we'll get back to you just as soon as we can.
Cleanroom contamination is a recurring problem for all our clients. Use this guide to keep your cleanroom as contaminant-free as possible.
We've learned the ins and outs of proper clean-room wipe-down techniques and in this article, we share them with you. You might be surprised that some of your tried-and-true techniques for cleaning other surfaces just don't apply when it comes to keeping your cleanroom clean and as contaminant-free as possible.